Generator Test Load Bank (PF0.8)
|FOB Price:||US $80,000-120,000 / Piece|
|Min. Order:||1 Piece|
|Min. Order||FOB Price|
|1 Piece||US $80,000-120,000/ Piece|
|Production Capacity:||500 Unit|
|Payment Terms:||L/C, T/T, Western Union|
- Model NO.: AC400-2000KVA
- Installation Method: Fixed
- Cooling Method: Air Cooled
- Speed: Speed
- Landuse Type of Unit: Ordinary
- Voltage: 400V
- PF: 0.8
- Cooling: Air Cooled
- Resistor: Metal Alloy
- Container: ISO
- Transport Package: Container
- Origin: China
- Type: Micro-Computer Control Automatic Diesel Generator
- Stroke: No
- Output Type: AC Three Phase
- Conditions of Use: Land Use
- Excitation Mode: AC Rotating Exciter
- Power: 2000kVA
- Frequency: 50Hz or 60Hz
- Technology: Metal Alloy
- Protection: IP54
- Trademark: Triumph Load
- Specification: Standard
- HS Code: 903033900
Dry-type Load Bank,The machine can test output power and load capacity of generator. Load cabinet power input with sub-type, be remotely controlled and extremely easy to use. Load bank use energy method, air forced cooling, the fan with three-phase fan air dispersion, so that machine noise is reduced greatly.
(1) Steady-state Test: Power can be loaded within a predetermined value, and is able to test and real-time display the power source voltage, current, power factor, frequency, time, reactive power, active power, apparent power, temperature resistance, resistance load rate of change, the rate of change of the load reactance and the reactor phase imbalance and other real-time, In addition storage, data output. Transient and historical data can be displayed.
(2) Setting Test: Capture voltage, frequency setting maximum, minimum, and calculate the relative voltage, frequency up, down range and regulation.
(3) Fluctuation Test: Capture voltage, frequency setting maximum, minimum, and calculate the steady-state frequency band, the steady-state voltage deviation, voltage modulation, volatility and frequency.
(4) Sudden test: Capture transient voltage, current, frequency, maximum, minimum, and recovery time when the load mutation. Calculate the transient voltage deviation sudden and transient frequency difference.
(5) Suddenly unloaded test: Capture transient voltage, current, frequency, maximum, minimum and recovery time when the load mutation. Meanwhile calculate the transient voltage deviation sudden and transient frequency difference.
(6) Power regulation: load power from smallest to maximum. (this feature can be based on our existing equipment to adjust the section software).
(1) Control: local control, remote control (control mode switch on the control panel of device).
(2) Local control: The machine with local control panel, and carved out a number of power steps, control loading by switch, displaying test parameters by measuring instruments.
(3) Remote manual control: Remote control by remote box or intelligent control bench.
(4) Remote intelligent control: Data management software control load bank by computer or smart control bench, achieve all the test functions, and test data display, recording and management, generate various curves, charts, test reports, and support for printing.
(5) Control mode interlock: System equipped with a control mode selector switch, to select any one of the control mode, the else control will be locked
(6) Parallel machine: Each machine can be controlled by control devices under local control and remote control, and displayed real-time parameters of all the machines, by upgrading our existing equipment meet with our existing equipment simultaneously load and machine. Requirements are as follows:
1) Through the transformation of our existing multi-load equipment hardware or software, implementation and use of newly purchased equipment and machines, to add and subtract carrier synchronization, and the ability to display the load parameters.
2) Require manufacturers to inspect determined by the manufacturer shall not subcontract the work to complete the transformation.
3) The new equipment delivery within 60 days to complete the transformation of all existing equipment.
4) Connecting the old and new devices can communicate and meet the functional user requests.
(7) Control selection: Load control and remote control either-or, manual control and intelligent control either-or, avoid chaotic control.
(1) Communication: Intelligent control the use of opto-isolated RS485 communication port connecting the PC. You can also use the USB or RS232 communications port.
(2) Loading: Steady-state load (manual loading, pre-loaded, automatic loading); transient load (sudden unload).
(3) Manually load: input power and power factor, which is loaded by the specified value.
(4) Pre-loaded: Enter the generator set parameters, you can select 0%, 25%, 50%, 75%, 100-110% preset ratios, etc., automatically calculate the appropriate power for fast loading.
(5) Automatically load: You can set multiple stages of power load test time long, automatic test phase. The loading process can pause, or skip to the next stage.
(6) Step Load: In steady-state loading process, the load will gradually increase or decrease, a smooth transition to the target power, avoid unplanned sudden load unload, step interval values can be set free.
(7) Power Compensation: You can enter the resistance through software to compensate for line material, length and other causes of power loss.
(8) Parallel Machine Test: multiple load and machine can be tested, and the machine is running, you can display and record the parameters of each station loads, also display, record the total system after paralleling machine.
(9) Automatically: load and subtraction and addition and subtraction operations manual, can be set to load and run the program according to user needs.
(1) Real-time Monitor: Software display main parameter value, such as voltage, current, power, power factor, frequency and time.
(2) Data Collection Interval: the minimum steady-state data resolving time is 1 second, and the minimum transient data resolving time is 40μs.
(3) Stable Data Comparison: the max value and min value of all the parameters in steady-state test is listed in software interface, which is convenient for user to compare.
(4) Data Save and Query: All test data be saved in the software, according to generator set number, easy and fast check the history test data.
(5) Graphical Display: show real-time or history test data, and support to print curve and graph as follows:
1) Voltage, current, frequency and power curves in real-time; 2) voltage curve;
3) Current curve; 4) power curve; 5) frequency curve; 6) power factor curve;
7) Instant load voltage curve; 8) instant load current curve;
9) Instant load frequency curve; 10) instant unload voltage curve; 11) instant unload current curve; 12) instant unload frequency curve; 13) voltage harmonic curve;
14) voltage harmonic histogram; 15) current harmonic curve; 16) current harmonic histogram; 17) wave record curve
(6) Test Report: display and support to print reports as follow:
1) Test report of generator set steady-state performance;
2) Transient test report;
3) Testing data report
(7) Data Format: all curves and graphs are outputted as".jpg"format, testing reports are outputted as".xls"format, and print is available.
(1) Protection: loss of pressure, over-voltage protection, short circuit, over current protection, thermal protection, smoke protection, fan flow protection, insulation monitoring, emergency stop.
(2) Emergency Stop: a key to force uninstall manually under any control on-site emergency stop buttons are priority control, stop locked state can not be loaded.
(3) Temperature Protection: device is equipped with a temperature sensor, the event will appear outlet over temperature fault indication, the fault indication is issued, as the temperature continues to rise to a preset temperature corresponding to the load is automatically unloaded, does not affect the normal use of other loads.
(4) Fan Flow Protection: The device is equipped with pressure detection, overvoltage occurs once the outlet, under voltage malfunction indication, then automatically unload and load the corresponding fan.
(5) Security Monitoring: Equipment with perfect protection and alarm detection systems, each alarm and current working status can be displayed through the sly operating room, or by remote control display, intuitive monitoring of load conditions, abnormal shutdown protection, suggesting causes of downtime.
(6) Status Display: All interlock function, power switching status, control status, etc. should be equipped with the appropriate status indicator.